This material may consist of step-by-step explanations on how to solve a problem or examples of proper writing, including the use of citations, references, bibliographies, and formatting. This material is made available for the sole purpose of studying and learning - misuse is strictly forbidden.
PV modules needed:
The total consumption per day = 1.092KWhr
Hence the actual supply needed from the PV panels = 1.3 * 1.092KWhr = 1.4196KWhrs.
Watt-peak hours needed = 1.4196/3.43 = 0.414KWhr =414Whr-Peak
The actual rating of the PV modules available = 110Wp
Hence the number of PV modules needed =414/110 ~ 4 PV modules are needed.
Inverter rating should be sum of all the ratings of the appliances = (18+3*60+3*75) = 423W~ 425W
Inorder to account for the surge currents during the starting, the inverter capacity is accounted for three times the motor start up as per the needs of the fan and the refrigerator capacities....
This is only a preview of the solution. Please use the purchase button to see the entire solution